5120F Hard Panel Fire System
Everything You Need For Entry Level Enclosure Integrity Testing1 x Panel Case with Shoulder Strap 33x33x7
1 x Fan Panel for 5000/6000 Fan Series
1 x Large Fill-in Sheet for Fan Panel
1 x Small Fill-in Sheet for Fan Panel
1 x Large X Panel
1 x XY Panel
1 x Fan Safety Strap for Modular Panel for 5000/6000 Fans
Test for hold times in flooded volumes up to 35,000 cu ft (1000 m3) for Inert agents and 70,000 cu ft (2000 m3) for halocarbon chemical agents.
This system will test the venting for a volume up to a maximum of 9,000 cu ft (250 m3) for Inert agents although vents up to 6 sq ft (0.6 m2) can be measured individually.
Request literature on all of Retrotec systems to determine the size of enclosures that can be tested with each system.Testing pressure relief vents will require more power.
Why Retrotec for Enclosure Integrity?
All Retrotec systems include tech support from Retrotec who originated the idea of Enclosure Integrity testing in 1984. They promoted it within NFPA and in 1986 wrote the first Enclosure Integrity standard. Retrotec has been the lead researcher for enclosure testing ever since. Every major clean agent system manufacturer worldwide relies on Retrotec’s expertise for both hold time and peak pressure predictions.